The Extreme 8000ti handles approximately 2000 cubic ft when cellar is fully insulated and
sealed with proper vapor barrier. Each
cellar is unique and has specific cooling requirements so please contact us if
you need assistance with heat load calculations. If glass walls or glass doors are installed
in the cellar, a stronger system is typically recommended.
value is 6131
The Exteme ti Series is intended for through-the-wall
installations and is visible in the cellar.
The controller is mounted in front of the cooling unit. This is a more economical option compared to
the ducted or split cooling unit options since a licensed AC tech is not required
to install. Common areas these units can
vent to – garages, outside, mechanic rooms, or any adjacent room that is at
least twice the size of the cellar and has fresh air flow. The area venting out to should not exceed 110
If this unit will be installed through an exterior wall, you will need
to purchase the exterior housing grill to protect the unit. If the unit will be installed through an
interior wall, you can duct the hot air exhaust (condensing side) and redirect
to another location.
Insulation – We recommend minimum R13 for the walls and R19 in the
ceiling. The higher the insulation the
less the cooling system will have to run. A vapor barrier is required on the warm side
of the cellar before the insulation. If using closed cell spray foam insulation for
all walls and ceiling, that also acts as a vapor barrier, so you do not have to
install the plastic barrier. For more detailed information you can view the video link below on 'how to prepare your wine cellar'.
Dimensions: 28”L x
14.25”W x 22.75”H / 115lbs
rating: 115v (20amp dedicated circuit required)
venting to should not exceed 110 degrees.
If venting outside, the exterior grill should be ordered. Condensing side can be ducted with purchase
of duct kit.
year limited warranty (parts and labor) 5 year warranty on compressor
View Installation Manual
View Extreme Series Specifications